PSI HW Calculator
Sunday, August 4, 2013
Comparison of the H2OMAP SWMM5 Hazen Williams Force Main Solution to a HW Solution
Note: Comparison of the H2OMAP SWMM Hazen Williams Force Main Solution to a HW Solution
In this example, we compare the force main head loss in four links in H20Map SWMM to the head loss in a steady state HazenWilliams solution for the same length pipe, diameter and flow (Figure 1). The H2OMap SWMM model has a large constant dry weather inflow at the wet wells which floods the wet well and causes a constant pump flow to the force main (Figure 2). TheHW calculator is located here http://www.engineeringtoolbox.com/william-hazens-equation-d_645.html and a comparison forHW head loss in PSI for 5000 feet long, 3 inch diameter pipes with HW Coefficients of 130, 120, 110 and 100, respectively, is shown in Table 1. The SWMM 5 equation loss (PSI Diff) and the PSI loss from the HW calculator are very close for all four links.
Table 1. Steady State comparison between HW Calculator and H2OMAP SWMM/SWMM 5 Force Main calculations.
Figure 1. H2OMAP SWMM Wet Well, Pump, Force Main and Gravity Main Network.
Figure 2. Constant Pump Flows
GIS Gateway – Create Shapefile T he Create Shapefile tool available from the GIS Gateway , allows you to create a new ESRI® Shapefile dir...
Comment: A really nice water analogy for the field properties Divergence, Curl and Gradient from the Blog Starts With a Bang ....it&...
Engine Error Number Description ERROR 101: memory allocation error. ...
Soffit Level ( pipe technology ) The top point of the inside open section of a pipe or box conduit. The soffit is the ...